You have no items in your shopping cart.
|United States/Heaters: Downflow Forced Fans/2600 Series Downflow Unit Heater Roof Mounted with Linear Louvered Diffuser, Bracket and Thermostat
|Spec Sheet (.pdf)
|General Characteristics 2600 Series Downflow Unit Heater Roof Mounted Linear Louvered Diffuser, Brac
|The contractor shall furnish and install the 2600 Series electric vertical discharge unit heaters of the size, capacity and voltage specified. Heaters shall be installed according to the manufacturer’s recommendations and applicable national and local codes.
Elements shall consist of Nickel Chromium alloy resistance wire embedded and completely surrounded in Magnesium Oxide, enclosed and swagged into corrosion resistant sheaths. Corrosion resistant steel fins shall be permanently attached to the sheaths to provide maximum heat transfer to the air stream.
Motors shall be single phase, resilient mounted, totally enclosed, industrial rated with an automatic reset thermal overload protective device. Motors on heaters up to 20 KW capacity shall be permanently lubricated shaded pole type. Over 20 KW, motors shall be permanent split capacitor type. Motors shall be mounted out of the main air stream in such a manner as to allow ambient air to be drawn over the motor to reduce motor temperature. Motor shall be separately removable from beneath the heater without removing the entire heater from mounting bracket.
Fan blades shall be heavy-duty individually balanced axial flow type. Fan speed shall not exceed 1570 RPM.
All heaters shall be equipped with a manual reset thermal cutout which disconnects elements and motor in the event normal operating temperatures are exceeded.
Heaters shall be designed for a single supply circuit with elements, motor and control circuits subdivided and fused to conform with the latest National Electric Code and OSHA requirements. All three phase heaters shall have balanced phases.
Heaters shall be controlled by a low voltage wall mounted thermostat. All heaters 25 KW and larger shall be wired for 2 stage operation. 5 KW through 20 KW units are single stage. All heaters shall be equipped with a fan safety device that causes fan to operate after elements are de-energized to purge unit of residual heat.
Includes Diffuser, Bracket and Thermostat
|Product Applications 2600 Series Downflow Unit Heater Roof Mounted Linear Louvered Diffuser, Bracket
|Recommended for all industrial, commercial, and residential. For indoor and outdoor use.
|Warranties 2600 Series Downflow Unit Heater Roof Mounted Linear Louvered Diffuser, Bracket and Therm
|Manufacturer's Limited Warranty: 1 Year.
|Keywords and Search Terms
|2600 series for ceiling mounting, 2600 series heater with thermostat, Axial heavy duty fans with Bracket, Ceiling Mount Heater with Bracke, Ceiling Heater with thermostat, 2600 Series Standard Heater, 2600 Series shown with standard, 2600 Series Heater with diffuser, Heater Heavy duty fan with diffuser, 2600 series heavy duty fan, Heater for Industrial 2600 series, Sturdy Heater for Ceiling, Chemical Resistant Heater, Ceiling fan Heater with diffuser, 2600 Series Flow Fan Contact Now, Ceiling Flow Unit Heater with Brack, Heater with 24 volt control, Heaters Equipped with diffuser, Heater of the 2600 series, 2600 series ceiling heater, Heater of the 2600 series, Shown with standard wire guard, 2600 Series Downflow Unit Heater, Heater 2600 series heavy duty fan, Heater for chemical work, Heater Fan for Rough Use, Heater for Industrial with thermost, 2600 series heavy duty heater, 2600 series ceiling fan heater, Recessed ceiling heater with Bracke